Ultra Loud 125 db Sump Siren Type Alarm with Flashing LEDs. Illuminated red mute button allows you to silence the alarm. #smpa3
Indoor/Outdoor High Water Alarm with 10 foot AC line cord, 12-foot Float cord ( 12 foot available), Red LED push on push off mute button, when muted the switch glows red. The case is waterproof with rubber seals. Tonal Alarm for Septic / Sump / Pond & Other Applications.
Monitor your outdoor pump or Septic System Level from a remote location. A piercing audible notification when a pump is non-operational. The alarm will sound and flash when a high water or pump failure situation occurs. The alarm can be silenced with the mute button which will glow red when muted.
Applications Include: Septic Systems - Outdoor Sump Pump Alarm / Crawl Space Pump Failure - Outdoor Sump Pump Monitor / Septic Pump Failure Alarm - Swimming Pool Sump Pump Monitor / Sump Pump Alarm System - 120/ 220 Volt Sump Pump Failure Alarm / Sump Pump Failure Warning - Sump Pump Alert
When a high level alarm condition exists, Ultra Loud 125 db tonal alarm and flashing LEDs become active. Place the float by your pump water well, mount the alarm unit, plug in the unit, and the installation is complete. The alarm unit can be up to 10 feet away from the 110 Volt outlet.
Includes sump alarm counter weigh.
Waterproof Alarm unit- Wall or panel mount.
Has (2) rear mounting holes for mounting
Includes wall anchors for head unit, zip ties for floats, and instructions
Mercury Free Float Switch is suitable for use with potable water
It can be used in sump pumps, water tanks, lift stations, low density oils and sewage water
Unit is wired for high level alarm, but can be reversed for low level alarm
110 / 220 volts AC power unit with 10 foot low voltage cord.
12 volt battery backup can be attached.
How it works:
The alarm has a float on a line cord. On the line cord there is an adjustable weight. The weight slides on the cord and is placed in the well at the level you want the alarm to sound. The float switch is hanging below the weight. When the liquid rises to the high level of the float switch activates the alarm. This indicates that the liquid has reached an alarm point indicating pump failure.